Post Number: 148
|Posted on Sunday, December 12, 2010 - 10:01 pm: |
Is the current (2010) building code for electrical outlets not more than 6ft on an unbroken wall (12 feet max wrapping around wall at corners)?
Also, in a laundry room, should there be at least one outlet? There is a single outlet for a dryer and a single (one not dual) outlet for the washer. Does this meet building code?
Ben Brezina, Assistant to the City Manag
Post Number: 68
|Posted on Monday, December 27, 2010 - 11:01 am: |
Receptacles shall be installed so that no point measured horizontally along the floor line in any wall space is more than 6 feet, from a receptacle outlet.
The only required outlets for laundry rooms are for the appliance laundry equipment.
Asst. Building Official